I recently came across a nice data center cooling design by Alan Beresford of EcoCooling Ltd. In this approach, EcoCooling replaces the CRAC units with a combined air mover, damper assembly, and evaporative cooler. I’ve been interested by evaporative coolers and their application to data center cooling for years and they are becoming more common in modern data center deployments (e.g. Data Center Efficiency Summit).
An evaporative cooler is a simple device that cools air through taking water through a state change from fluid to vapor. They are incredibly cheap to run and particularly efficient in locals with lower humidity. Evaporative coolers can allow the power intensive process-based cooling to be shut off for large parts of the year. And, when combined with favorable climates or increased data center temperatures can entirely replace air conditioning systems. See Chillerlesss Datacenter at 95F, for a deeper discussion see Costs of Higher Temperature Data Centers, and for a discussion on server design impacts: Next Point of Server Differentiation: Efficiency at Very High Temperature.
In the EcoCooling solution, they take air from the hot aisle and release it outside the building. Air from outside the building is passed through an evaporative cooler and then delivered to the cold aisle. For days too cold outside for direct delivery to the datacenter, outside air is mixed with exhaust air to achieve the desired inlet temperature.
This is a nice clean approach to substantially reducing air conditioning hours. For more information see: Energy Efficient Data Center Cooling or the EcoCooling web site: http://www.ecocooling.co.uk/.