I frequently get asked “why not just put solar panels on data center roofs and run them on that.” The short answer is datacenter roofs are just way too small. In a previous article (I Love Solar But…) I did a quick back of envelope calculation and, assuming a conventional single floor build with current power densities, each square foot of datacenter space would require roughly 362 sq ft of solar panels. The roof would only contribute roughly 1% of the facility requirements. Quite possibly still worth doing but there is simply no way a roof top array is going to power an entire datacenter.
There are other issues with roof top arrays, the two biggest of which are weight and strong wind protection. A roof requires significant re-enforcement to support the weight of an array and the array needs to be strongly secured against strong winds. But both of these issues are fairly simple engineering problems and very solvable. The key problem with powering datacenters with solar is insufficient solar array power density. If we were to believe the data center lighting manufacturers estimates (Lighting is the Unsung Hero in Data Center Energy Efficiency), a roof top array wouldn’t be able to fully power the facility lighting system. Most modern data centers have moved to more efficient lighting systems but the difficult fact remains: a roof top array will not supply even 1% of the overall facility draw.
When last discussing the space requirements of a solar array sufficient to power a datacenter in I love Solar but …, a few folks took exception to my use of sq ft as the measure of solar array size. The legitimate criticism raised was that in using sq ft and then computing that a large datacenter would require 181 million sq ft of solar array, I made the solar farm look unreasonably large. Arguably 4,172 acres is a better unit and produces a much smaller number. All true.
The real challenge for most people is in trying to understand the practicality of solar to power datacenters is to get a reasonable feel for how big the land requirements actually would be. They sound big but data centers are big and everything associated with them is big. Large numbers aren’t remarkable. One approach to calibrating the “how big is it?” question is to go with a ratio. Each square foot of data center would require approximately 362 square feet of solar array, is one way to get calibration of the true size requirements. Roughly 100:1 which tells us that roof top solar power is a contributor but not a solution. It also helps explain why solar is not a practical solution in densely packed urban areas especially where multi-floor facilities are in use.
The opening last week of the Kagoshima Nanatsujima Mega Solar Power Plant is large array at over 70MW and it gives us another scaling point of land requirements for large solar plants:
· Name: Kagoshima Nanatsujima Mega Solar Power Plant
· Location: 2 Nanatsujima, Kagoshima City, Kagoshima Prefecture, Japan
· Annual output: Approx. 78,800MWh (projected)
· Construction timeline: September 2012 through October 2013
· Total Investment: Approx. 27 billion yen (approx. 275.5 million U.S. dollars*4)
This is an impressive deployment with 70MW peak output over 314 acres. That’s roughly 4.5 acres/MW which is fairly consistent with other solar plants I’ve written up in the past. The estimated annual output for Kagoshima is 78,800MWh which is, on average, 9MW output. The reason the expected average output is only 13% of the peak output is solar plants aren’t productive 24×7.
Datacenter power consumption tends to be fairly constant day and night. Night being somewhat lower due to typically lower cooling requirements. But with only 10 to 15% of the total power in a modern datacenter going to cooling, the difference between day and night is actually not that large. Where there are big differences in datacenter power consumption is in the power consumption at full utilization vs partial. Idle critical loads can be as low as 50% of full loads so some variability in power consumption will be seen in a datacenter but datacenters are largely classified as base load (near constant) demand. Using these numbers, the Kagoshima solar facility is large enough to power ½ of a large datacenter.
The Kagoshima Nanatsujima Mega Solar Power Plant is a vast plant and anything at scale is interesting. It’s well worth learning more about the engineering behind this project but one aspect that caught my interest is there are some excellent pictures of this deployment that do a better job of scaling that my previous “several million sq ft” reference. The Kagoshima array is 313 acres which is 13.6 million sq ft or 1.27 million sq meters but these numbers aren’t that meaningful to most of us and pictures tell a far better story.
Above Photos from: http://global.kyocera.com/news/2013/1101_nnms.html
No matter how you look at it, the Kagoshima array is truly vast. I’m super interested in all forms of energy production and consider myself fairly familiar with numbers on this scale and yet I still find the size of this plant when shown in its entirety to still be surprising. It really is big.
The cost of solar is falling fast due to deep R&D investment but a facility of this scope and scale is still fairly expensive. At US$275 million the solar plant is more expensive than the datacenter it would be able to power.
Despite the shortage of land space in Japan, expect to see continued investment in large scale solar arrays for at least another year or two driven by the Feed-in Tariff legislation which requires Japanese power companies to buy all the power produced by any solar plant bigger than 10kW at a generous 20 year fixed rate of 42 yen/kWh which at current exchange rates is US$0.42kWh (Japan Creates Potential $9.6 Billion Solar Boom with FITs and also 1.8GW of New Solar Power for Japan in Q2). As a point of comparison, in the US commercial power, if purchased in large quantities is often available at rates below $0.05/kWh.
Yano research institute predicts that the massive Japanese solar boom driven by the FIT legislation will be grow until 2014 and then taper off due to land availability pressure: Japan Market for Large-Scale Solar to Drop After 2014, Yano Says.
One possible solution to both the solar space consumption problem and the inability to produce power in poor light conditions are orbital based solar arrays (Japan Aims to Beam Solar Energy Down From Orbit). This technology is nowhere close to a reality today but it is still of interest.
More articles on the Kagoshima Nanatsujima Mega Solar Power Plant:
For those of you able to attend the AWS re:Invent conference in Vegas, I’ll see you there. I’ll presenting Why Scale Matters and How the Cloud Really is Different Thursday at 4:15 in the Delfino room and I’ll be around the conference all week.